|Alarm meaning||Fan motor trouble|
|Alarm conditions||Fan motor start failure, fan motor Hall IC input failure|
|Probable cause||Possible causes are a Hall IC input circuit failure and a fan HIC failure.|
Check the fan motor wiring, the Hall IC wiring, and the connector connections. If the wiring and connectors are normal, then check that the capacitor of the Hall IC input circuit is securely soldered onto the PCB. Also use a tester and measure the resistance between fan HIC power (HIC+) and ground (HIC–). If there is a short circuit, there is an HIC malfunction.
Fan circuit on the outdoor unit control PCB
* In the 3-WAY SYSTEM, the fan circuit PCB is integrated with the outdoor unit PCB.
If the fan does not start, the below corrections may be effective.
|Notes||Turn OFF the power, and check the continuity of “+” and “–” on the fan circuit PCB.|